MERV A13 Performance Data
> Air Velocity for ASHRAE Testing: 492 fpm (1968 cfm for 24" x 24" filter)
> Initial Pressure Drop: 0.39" w.g.
> Recommended Final Pressure Drop: 1.4" w.g.
> Efficiency Rating per ASHRAE 52.2: 2007: MERV 14¹
> Efficiency Rating per ASHRAE 52.2: 2007 Appendix J: MERV A13
>Dust Holding Capacity at 1.4" w.g.: 95 ± 7 g
■ Reliable performance in the most extreme commercial office building HVAC environments due to durable, moisture and humidity resistant, 100% synthetic filtration media, 100% metal free filter design and engineered frame construction.
■ Significant energy savings possible when installed in place of standard filters due to low pressure drop achieved through the use of this highly refined electrostatically charged media(electret media), open filtration media structure and high surface area mini-pleat design.
■ Far less storage space required compared to many filters of same efficiency resulting from thehigh performance 2” mini-pleat filter format.
■ Reduced labor hours
■ The 3M Commercial HVAC Filter MERV A8, MERV A11 and MERV A12 contribute to earning a point in the LEED® certification process during the construction phase for new buildings and renovations.
■ The HVAC filter meets UL 900 Class 1 (US) flammability rating.
Other Similar Products/Services